The PIV fan shall be of positive inducing type mounted with a galvanized centrifugal steel wheel. It shall undergo static and dynamic balancing tests and reach AMCA 204- G2.5 balancing level.
Constructed of galvanized steel panels (optional: treated with electrostatic epoxy coatings), the fan housing is designed to prevent corrosion. An access door shall be mounted and easily removed for maintenance and inspection. At the outlet, baffle plates shall be fitted to ensure even discharge from each nozzle.
There shall be a close match between the motor and the fan load. It shall have a degree of protection standard IP44, and an insulation class F. The motor shall be of direct drive type.
The nozzle shall be directly mounted on the housing. It shall be of a flexible type and spun seamlessly with aluminum alloys.
Thank you for visiting INFINAIR CORPORATION’s website. Please share your information below and we will gladly respond to your request.